L’ accoppiatore KNX RF/TP 673.1 secure è un accoppiatore radio KNX compatto. Collega i dispositivi RF KNX di una linea radio con il doppino twistato del bus KNX.
Il dispositivo dispone di una tabella filtri estesa per il gruppo principale 0 … 31. L’accoppiatore supporta frame lunghi ed è compatibile con il software ETS® di ETS 5.
I pulsanti sulla parte anteriore consentono di disattivare il filtro dei telegrammi a scopo di test. I LED indicano gli stati di funzionamento e gli errori di comunicazione sul bus.
L’alimentazione è fornita tramite il bus KNX.
Il dispositivo supporta KNX Data Security. La funzionalità Security Proxy e Segment Coupler è supportata solo con il database ETS 6.
KNX ENO 626 secure
The KNX ENO 626 secure device serves as a bidirectional gateway between EnOcean wireless devices and the KNX bus. With this device, commands and measured values from EnOcean wireless sensors can be transmitted to the KNX bus, for example to control KNX actuators. EnOcean wireless actuators can also be controlled via KNX. The KNX ENO 626 secure from Weinzierl supports the encrypted radio communication with security-enabled EnOcean devices.
In addition, the gateway provides logic and control functions and includes a wireless repeater. The KNX ENO 626 secure now supports more than 100 profiles with its 8 radio channels, allowing the easy and secure connection of even more different EnOcean sensors and actuators KNX installations.
As the first KNX gateway in the market, the new KNX ENO 626 secure supports the encrypted radio communication with EnOcean devices. Commissioning is as simple as usual: with all 8 channels encryption can be activated individually. Subsequently EnOcean sensors and actuators, which support security, can be taught as before. The user gets more security without loss of comfort.
Broad variety of functions in a small case
The KNX ENO 626 secure has 8 channels, which can be used with one of the following functions from over 100 profiles (EEP EnOcean equipment profiles):
Link from EnOcean sensor to KNX:
Switching and contact functions
access cards switches
push button switches
Room control devices
Automated counter devices
Environmental sensors (weather station)
Link from KNX to EnOcean actuator:
HVAC actuators (valves)
Control / logic:
Two point controller (byte and float)
Heat demand requirements
Gates (e.g. AND, OR, XOR)
The configuration of the device and the channels is done using the ETS software via the KNX bus. For the teach-in of the wireless components the keys and the LEDs on the device are used.
Mounting and connection
The mounting can be done in a 68 mm flush-mounted box. The power supply of the device is realized via the bus.
The repeater function is used for extend distances between sensors and actuators. The KNX ENO 626 is a so-called level-1 radio repeater.
Configuration: KNX ENO Tool
The KNX ENO Tool software can be used to configure the Links between various EnOcean-Sensors and the KNX/EIB EnOcean-Gateway KNX ENO 626/630/632/6347636. The device configuration of the Gateway can be read, modified, exported and saved back to either the same or another Gateway. EnOcean Bus Monitor showing the EnOcean Telegrams send over the KNX Bus.
KNX ENO Tool download.